Self Cleaning Filters
These are used where continuous flow and unassisted cleaning is required. They are designed for installations which will be unattended for extended time periods. It is suitable for a remote or difficult service locations.
The liquid to be filtered enters through the inlet connection and passes through the specially engineered wedge wire element with the flow being from outside to inside. Solids larger than the selected micron spacing are either retained on the outside of the filter element or drop into the filter chamber sump.
The filtered liquid then passes through the top of the element and flows out through the outlet connection.
As the filter element becomes progressively fouled by retained solids the differential pressure across the filter rises.
Element is cleaned by rotating top handle by manually or by motor and scraper is provided on the surface of the filter element which scrapes out impurities deposited on the element by three or four rotation of element gets cleaned and impurities can be removed by opening drain valve from bottom. Suitable for large volume and fine filtration upto 30 microns available with single or multi elements in Body carbon steel, SS 304, 316, 316L or any other alloy steel material.
Liquid enters from the inlet, passes through the filter element and gets out of the outlet of the Filter Nozzle. Differential Pressure (DP) Switch is provided across the Inlet and Outlet of Filter. When the Filter Element gets choked Pressure Drop across the filter increases. Normally maximum Differential Pressure for backwashing is set at 0.5 Kg/cm2. When the Differential Pressure reaches the set limit the DP Switch gives a signal to the Control Panel (CP) and the CP gives a signal to the Motor and Electrically or Pneumatically Actuated Drain Valve. The Motor connected to back wash arm starts rotating 3600 with 10 – 15 RPM; simultaneously the Motorized Drain Valve also gets opened to the atmosphere.
Backwash Arm is a hollow pipe and is connected directly to the Electrically Actuated Drain Valve. Whenever the open portion of the Backwash Arm comes in front of the Element a heavy Differential Pressure is created between the Backwash Arm and the Filter element. The water starts flowing in reverse direction from Filter Element towards Backwash Arm since the valve is open to the atmosphere. During this process all the impurities collected inside the Filter Element get sucked and discharged through the Drain Valve. In 4- 5 rotations the Filter Element gets cleaned. Normal duration of backwash cycle is 30- 40 seconds and the loss of water during backwash is around 2- 3% of the inlet water quantity. Manual drain valve is also provided to clean the filter.
A Timer (Range 0 to 24 hrs) is provided in the Control Panel which is normally set for 2- 3 hours. In case the Differential Pressure does not reached the set limit in that duration the Timer gives a signal to the Control Panel and the Backwash Cycle gets initiated. There is also a Selector Switch provided in the Control Panel so that when you need to operate the Backwash Operation manually you can change the selector switch and have the Backwash Operation by Push Button. Auto Backwash Filter system is a fully Automatic and is meant for removal of contaminants from fluids in the pipe line system. The Filter has simple construction and the fully automatic back flushing not only guarantees a high operating safety but also keeps running cost to the minimum
Technical Specifications: Motorised Self- Cleaning Filters (Manual or Automatic), Automatic Backwash Filters / Automatic Self Cleaning Filters
|Size||Rating||Material of Construction|
|15 NB to 1000 NB||150#, 300#, 900#, 1500#||Carbon Steel, Stainless Steel and Alloy Steel, in welded construction Automatic operation with control panel (relay based, PLC based and start up panel), option of automatic drain
valve which can be pneumatic or electrical operated